Heat Recovery 101: Exhaust gas loss or waste heat depends on flue gas temperature and its mass flow, or in practical terms, excess air resulting from combustion air supply and air leakage into the furnace. The excess air can be estimated by measuring oxygen percentage in the flue gases.
Waste Heat Recovery
Heat losses must be minimized before waste heat recovery is investigated. The most commonly used waste heat recovery methods are preheating combustion air, steam generation and water heating, and load preheating.
Preheating Combustion Air
A recuperator is the most widely used heat recovery device. It is a gas-to-gas heat exchanger placed on the stack of the furnace that preheats incoming air with exhaust gas. Designs rely on tubes or plates to transfer heat from the exhaust gas to the combustion air and keep the streams from mixing
Another way to preheat combustion air is with a regenerator, which is an insulated container filled with metal or ceramic shapes that can absorb and store significant thermal energy. It acts as a rechargeable storage battery for heat. Incoming cold combustion air is passed through the regenerator. At least two regenerators and their associated burners are required for an uninterrupted process: one provides energy to the combustion air while the other recharges.
Steam Generation and Water Heating
These systems are similar to conventional boilers but are larger because the exhaust gas temperature is lower than the flame temperature used in conventional systems. Waste heat boilers can be used on most furnace applications, and special designs and materials are available for systems with corrosive waste gases. Plants that need a source of steam or hot water can use waste heat boilers, which may also work for plants that want to add steam capacity. However, the waste boiler generates steam only when the fuel-fired process is operating.
If exhaust gases leaving the high temperature portion of the process can be brought into contact with a relatively cool incoming load (the material being heated), energy will be transferred to the load, preheating it and reducing the energy consumption. Load preheating has the highest potential efficiency of any system that uses waste gases. Load preheating systems can be difficult to retrofit and are best suited for continuous rather than batch furnaces.
- Improved heating system efficiency. Energy consumption can typically be reduced 5% to 30%
- Lower flue gas temperature in chimney. Less heat is wasted.
- Higher flame temperatures. Combustion air preheating heats furnaces better and faster.
- Faster furnace startup. Combustion air preheating heats furnaces faster.
- Increased productivity. Waste heat used for load preheating can increase throughput.
Waste heat recovery should generally be considered if the exhaust temperature is higher than 1,000°F, or if the flue gas mass flow is very large. Contact us today to learn more about how a FLU-ACE direct contact condensing heat recovery system can help your business lower its fuel costs and reduce its carbon emissions.